Page 21 - ZSi-Foster-Engineering-Catalog

P. 21

```
Beam Load Support Formulas
All Beam Load tables are for simple beams supported at the ends. These can be used in the majority of the cases. There are times when it is necessary to know what happens with other loading and support conditions. Some common arrangements are shown below. Simply multiply the values from the Beam Load tables by factors given below.
Load and Support Condition
Load Factor
Deflection Factor
Simple Beam
Uniform Load
Span
1.00
1.00
Simple Beam
Concentrated Load at Center
0.50
0.80
Simple Beam
Two Equal Concentrated Loads at 1/4 Points
1.00
1.10
Beam Fixed at Both Ends
Uniform Load
1.50
0.30
Beam Fixed at Both Ends
Concentrated Load at Center
1.00
0.40
Cantilever Beam
Uniform Load
0.25
2.40
Cantilever Beam
Concentrated Load at End
0.12
3.20
Continuous Beam
Two Equal Spans - Uniform Load on One Span
Span Span
1.30
0.92
Continuous Beam
Two Equal Spans - Uniform Load on Both Spans
1.00
0.42
Continuous Beam
Two Equal Spans - Concentrated Load at Center of One Span
0.62
0.71
Continuous Beam
Two Equal Spans - Concentrated Load at Center of Both Spans
0.67
0.48
EXAMPLE I 60" 60" PROBLEM:
Calculate the load and deflection of an W200 beam continuous over one support and loaded uniformly on one span.
SOLUTION:
A. From load table for W200 the load for a 60" span is 700 lbs. and deflection is 0.35".
B. Multiply by factors from Table above Load = 700 lb. x 1.30 = 910 lbs. Deflection = 0.35 x 0.92 = 0.322".
EXAMPLE II
PROBLEM:
24"
ZSi-Foster Engineering Catalog
– 21 –
Determine load and deflection of an W150 cantilever beam with a concentrated load on the end.
SOLUTION:
A. From load table for W150 the load for a 24" span is 5,360 lbs. and deflection is 0.09".
B. Multiply by factors from Table above. Load = 5,360 lbs. x 0.12 = 643.2 lbs. Deflection - 0.09 x 3.20 = 0.288"
Technical Gamma Rooftop Concrete Beta Clamps Loop & Ring Spring Electrical Pipe & Conduit General Channel Nuts Channel Introduction Data Pads Supports Inserts & Z-Clamps Clamps Steel Fittings Supports Fittings & Hardware
```